Our VRLA Battery Maintenance services will help ensure that your back-up batteries will deliver maximum power when you need it most. As studies indicate, lack of maintenance is the major cause of premature battery failure. While valve regulated lead acid (VRLA) batteries require substantially less attention than traditional “wet” cell batteries, they do require maintenance.
VRLA Battery Maintenance: Planned maintenance programs that work for you
Designed to meet a range of telecommunications, UPS, and switchgear applications, our VRLA Battery Maintenance programs feature Internal Resistance Testing, which can be tailored to meet individual site or customer requirements. EnerSys performs all maintenance procedures recommended per IEEE Standard 1188, including all voltage, resistance, current and temperature measurements, a complete visual inspection, non-destructive impedance or resistance testing and a professional report summarizing the results. EnerSys will also work with you on any recommended course of action that may be necessary to ensure proper operation of your investment.
EnerSys offers two basic levels of planned maintenance services, both of which can be customized to meet your specific needs:
Basic Care – EnerSys performs all quarterly and annual maintenance as required by IEEE Standard 1188. All monthly measurements and inspections are the customer’s responsibility.
Maximum Care – EnerSys handles the total maintenance package, performing all monthly, quarterly, and annual maintenance procedures following IEEE Standard 1188.
|Measure and record overall float voltage|
measured at the battery terminals
|Measure and record charge output|
current and voltage
|Measure and record ambient temperature|
of battery room or cabinet
|Check condition of ventilation and|
|Visual inspection of cell/unit integrity for|
evidence of corrosion at terminals,
connections, racks, or cabinets
and area around battery for accessibility
|Check for excessive jar/cover distortion ||X||X||X|
|Measure and record DC float current|
(per string) using equipment that is
accurate to less than 1 A current
|Measure and record cell/unit internal|
|Measure and record temperature of the|
negative terminal of each cell/unit of battery
|Measure and record voltage of each cell/unit||X||X|
|Measure and record cell to cell and terminal|
connection detail resistance of entire battery
|Measure and record AC ripple current|
and/or voltage imposed on the battery